IMPORTANT INFORMATION ABOUT YOUR DRINKING WATER
Clover Hill III Water System – June 2019 Status Report
Our most recent sampling completed in May has shown the Clover Hill III water system remains in compliance for Haloacetic Acids (HAA5). The most recent calculation of the Locational Running Annual Average (LRAA) is below the federal Maximum Contaminant Level (MCL) of 60 parts per billion (ppb). The LRAA is calculated for each sample site by averaging test results from samples collected in February, May, August, and November of each year.
The LRAA for HAA5 calculated using May’s data is 41.8 ppb.
Next Steps –
Our staff will continue with our flushing efforts to keep HAA5 concentrations below the MCL and continue to collect samples to monitor HAA5 concentrations.
We are still awaiting the planned improvements to the treatment processes at the City of Frederick’s Fishing Creek water source and Lester Dingle Water Treatment Plant. Once complete, this project should result in further reductions in HAA5 concentrations.
We appreciate your patience and cooperation while we work to address this issue.
For more information, please contact the Frederick County Division of Utilities and Solid Waste Management at 301-600-1825.
The Metropolitan Washington Council of Government has information on preventing this from happening in your home on their Protect Your Pipes web page.
Request a Fire Hydrant Flow Test
Please complete the online Request for Fire Hydrant Flow Test. Your submission will be reviewed and you will be contacted with information about the processing of your request.